Project Site: Downey, California
Contact: Mitchell J Architecture, San Diego, California
At the time this electrical load report was written it was difficult to determine existing system capacity, since the facilities electrician restricted access to all panels despite the Engineer’s proposal of wearing Level 2 Arc Flash Personal Protective Equipment. Once the as-built electrical drawing became available we determined there was enough capacity for the LA-RICS radio site.
Whitcraft Engineering was able to develop the power design despite the restricted access by the facilities electrician.
Below: Fluke 1735 instrument temporarily installed in the panel to record the electrical load. These “Load Studies” last 30 days.