Project Site: Los Angeles County USC
Contact: Mitchell J Architecture, San Diego, California
One must use two meters and provide 2 load study for panel and one upstream panel per OSHPD PIN 38.
The upstream panel here is a substation US-L1 and the meter is built-in.
Notes Max Current was 161 Amps on phase C
occurred at an outage 10/1 44kW max
Measured Substation DTUS-L1
480/277V 3Phase 4Wire 800Amp 200kW
As-built drawings for circuit DT5LBA checked.
It is an 800 Amp circuit — there is enough additional power to run the 20kW LA-RICS system